- Reaction score
- Flowery Branch, GA
Just seeing this, sorry for the late reply. The check valve should go close to the sump. I'd be temped to put a true union ball valve above it. It will make maintenance of the check much easier.Just trying to eliminate the check valve bouncing. I am not sure if it matters either way, but am wondering if there is a preferred location.